Con-cur Dryer Booster Fan Control
The same control used in condo/apartment construction, this unit senses as soon as your clothes dryer draws more than 1 amp of current. It automatically turns on the booster fan, eliminating additional sensors, switches or speed controls. When current drops below the pre-set 2-amp threshold, the Con-Cur Dryer Booster Fan Control automatically shuts off the booster fan. Mount it:
1. inside your dryer compartment
2. at the dryer junction box, or
3. at the fuse/breaker panel
The dryer supply neutral (white) wire passes through the current transformer cutout with no physical connection to the control.
IMPORTANT: A licensed electrician is the best person to install this equipment. Be sure to adhere to local provisions and national electrical codes. Verify industry standards prior to installation.
|Input Range||1.25 – 40 Amp-turns|
|Hysteresis||<1% FS Max|
|Op.Temperature||0 – 40 °C (32-104°F)|
|Op. Humidity||0-95% RH Non-condensing|
|Trip Set-Point||Factory pre-set at approximately 1.25 Amps|
|Material||Self-Extinguishing ABS (Cycolac 94V-0)|
|HxWxD||70x89x28 mm (2.75×3.5×1.1 in) MAX|
|Mounting Holes||2x5mm holes spaced 76mm
(2×0.19 in. holes spaced 3 in.)
|AC Cond. Hole||19mm (0.75in) Ø|
|Switch Rating||120 VAC @ 2.5 Amps Max|
|Leakage Current||< 1mA|
|Core Current||1.25 – 40 Amps Continuous|
|INSTALLATION MODEL 1
1. Mount the Con-Cur current sensor in convenient location inside dryer connection compartment.
INSTALLATION MODEL 2
1. Attach electrical junction box to dryer junction box.